S-TECVINA CO., LTD
Address : Lô CN-03, Khu Công Nghiệp Đồng Văn IV, Xã Đại Cương, Huyện Kim Bảng, Hải Nam
Phone : 0226-2460-114
Email : email@example.com
The actuation cabinet STV-P1L is used to trigger the fire suppression system. The actuation cabinet STV-P1L can be used to actuate the FM-200 needle cylinder valve, or selector valves. It is also used to trigger the agent discharge alarm though the discharge pressure switch.
The actuation box assembly consists of a solenoid cutter, an CO2 pilot cylinder 1L 0.65kg, and a discharge pressure switch.
The actuation box assembly is enclosed in a steel box and factory pre-assembled.
The solenoid cutter is used to actuate the actuation cylinder.
It is an integral component of the actuation box and is activated via electric signal that is sent by the control panel (supplied separately) upon fire detection.
The solenoid cutter is fitted with PUSH button that is and should only be used for emergency manual activation should the electronics fail
The actuation cylinder is an integral part of the actuation box that is filled with 0.65kg of CO2.
The released actuation gas is then used to activate the corresponding FM-200 needle cylinder valve, or selector valves.
The actuation cylinder is factory-fitted with a discharge valve that is opened via the activation of solenoid cutter.
As part of the cylinder safety feature, the actuation cylinder valve is fitted with rupture disc-fitted safety plug to prevent unsafe pressure built-up and damage of the device.
DISCHARGE PRESSURE SWITCH
The discharge pressure switch is used to activate the discharge alarm system (supplied separately).
It is connected to the selection valve or discharge pipe via pressure switch actuation tube.
As the discharged extinguishing agent has reached the selection valve or pipe, pressure from the discharged extinguishing agent is used to activate the pressure switch.
The pressure switch is then used to allow the flow of electricity via electrical wires to activate the discharge alarm (system).