S-TECVINA CO., LTD
Address : Lô CN-03, Khu Công Nghiệp Đồng Văn IV, Xã Đại Cương, Huyện Kim Bảng, Hải Nam
Phone : 0226-2460-114
Email : firstname.lastname@example.org
Flexible discharge hose is used to connect the 82.5L FM200 cylinders to discharge piping or cylinder manifold. The hose has a thread fitting at both end.
The flexible discharge hose DN40 has welded with check vavle. . Check valve is mandatory requirement as item 126.96.36.199 TCVN 7161-1 when two or more cylinders are connected to the same manifold. Check valves shall prevent extinguishant loss from the manifold if the system is operated when any containers are removed for maintenance.
The stainless steel flexible braid hose may be installed horizontally or with a 90 degree bend radius as shown in the diagram below.