S-TECVINA CO., LTD
Address : Lô CN-03, Khu Công Nghiệp Đồng Văn IV, Xã Đại Cương, Huyện Kim Bảng, Hải Nam
Phone : 0226-2460-114
Email : email@example.com
Needle valve SFS-NV82.5 is used for trigger FM-200 cylinder 82.5L discharge. The needle valve SFS-NV82.5 will be installed on FM-200 cylinder actuation port. Pressurized actuation gas from the pilot cylinder is used to actuate the needle valve through copper tube / flexible actuation hose. The needle valve SFS-NV82.5 is equipped with a PUSH button that is used for manually actuation incase pilot system fail or operation by person.
The needle valve should be installed to FM-200 cylinder actuation port only when system has completed test and commissioning. The FM-200 cylinder discharge port has connected to system piping and cylinder has secured in place.
Never install needle valve to FM-200 cylinder with discharge port open. Fail to do this can make the incident discharge lead to not safe for person a rounding.